// CODE SNIPPET
418.2 Exhaust Requirements
JUMP TO FULL CODE CHAPTER
All air from the ETO sterilizer equipment room shall be exhausted to the outside by a dedicated system or other approved method.
The exhaust fan for the dedicated system shall be located at the discharge point of the system and identified as ETO Equipment Room Exhaust.
The discharge point shall be a minimum of 25 feet (7620 mm) away from any outside intake, operable window or personnel passage.
Related Code Sections
418.2 Ventilation Air, Exhaust Requirements
All air from the ETO sterilizer equipment room shall be exhausted to the outside by a dedicated system or other approved method ...
Los Angeles Mechanical Code > 4 Ventilation Air > 418.0 Design Requirements for Ethylene Oxide (Eto) Sterilization Areas > 418.2 Exhaust Requirements
507.1 Exhaust Systems, Exhaust System
Cooking equipment used in processes producing smoke or grease-laden vapors shall be equipped with an exhaust system that is in accordance ...
507.4 Exhaust Systems, Drawings
A drawing(s) of the exhaust system installation along with a copy of operating instructions for subassemblies and components used in the exhaust ...
507.5 Exhaust Systems, Notification of Change
Where required by the Authority Having Jurisdiction, notification in writing shall be given of an alteration, replacement, or relocation ...
Los Angeles Mechanical Code > 5 Exhaust Systems > 507.0 General Requirements > 507.5 Notification of Change