// CODE SNIPPET
317.6 Excessive Fires
JUMP TO FULL CODE CHAPTER
The occurrence of more than two fires in an automotive salvage and wrecking facility during any 12-month period shall give rise to a rebuttable presumption that the owner has failed to properly maintain the facility in compliance with the requirements of this section, and shall be grounds for revocation of department permits and other approvals, or other appropriate enforcement action.
Related Code Sections
4184.108.40.206 Special Detailed Requirements Based on Use and Occupancy, Hazardous Operations
fire area in excess of 1,600 gallons (6057 L). Total fuel capacity of all aircraft within the maximum single fire area in excess of 7,500 gallons ...
NYC Building Code 2014 > 4 Special Detailed Requirements Based on Use and Occupancy > 412 Aircraft-Related Occupancies > 412.4 Aircraft Hangars > 412.4.6 Fire Suppression > 4220.127.116.11 Hazardous Operations
718.104.22.168 Fire and Smoke Protection Features, Glazing in Doors
Fire-protection-rated glazing in excess of 100 square inches (0.065 m 2 ) shall be permitted in fire door assemblies when tested as components ...
NYC Building Code 2014 > 7 Fire and Smoke Protection Features > 715 Opening Protectives > 715.4 Fire Door and Shutter Assemblies > 715.4.4 Doors in Exit Enclosures and Exit Passageways > 722.214.171.124 Glazing in Doors
7126.96.36.199 Fire-Resistance-Rated Construction, Glazing in Doors
Fire-protection-rated glazing in excess of 100 square inches (0.065 m 2 ) shall be permitted in fire door assemblies when tested in accordance ...
NYC Building Code 2008 > 7 Fire-Resistance-Rated Construction > 715 Opening Protectives > 715.3 Fire Door and Shutter Assemblies > 715.3.4 Doors in Vertical Exit Enclosures and Exit Passageways > 7188.8.131.52 Glazing in Doors
Article 16 Sprinkler Systems [PDF] (page 3)
and not more than four hundred sprinklers in such average protected fire area, the available quantity of water in excess of 20,000 gallons need ...
903.2.3.1 Fire Protection Systems, Woodworking Operations
An automatic sprinkler system shall be provided throughout any Group F-1 occupancy fire area that contains wood working operations in excess of 2,500 ...
NYC Building Code 2008 > 9 Fire Protection Systems > 903 Automatic Sprinkler Systems > 903.2 Where Required > 903.2.3 Group F > 903.2.3.1 Woodworking Operations