# F 102.1 Example 4: Common Venting Two Draft Hood-Equipped Appliances

Solution:

Table 803.2(2) shall be used to size single-wall metal vent connectors attached to Type B vertical vents. In the vent connector capacity portion of Table 803.2(2), find the row associated with a 30 foot (9144 mm) vent height. For a 2 foot (610 mm) rise on the vent connector for the water heater, read the shaded columns for draft hood-equipped appliances to find that a 3 inch (76 mm) diameter vent connector has a capacity of 37 000 Btu/h (10.8 kW). Therefore, a 3 inch (76 mm) single-wall metal vent connector shall be used with the water heater. For a draft hood-equipped furnace with a 3 foot (914 mm) rise, read across the row to find that a 5 inch (127 mm) diameter vent connector has a maximum capacity of 120 000 Btu/h (35 kW) (which is too small for the furnace), and a 6 inch (152 mm) diameter vent connector has a maximum vent capacity of 172 000 Btu/h (50 kW). Therefore, a 6 inch (152 mm) diameter vent connector shall be used with the 150 000 Btu/h (44 kW) furnace. Since both vent connector horizontal lengths are less than the maximum lengths listed in Section 803.2.1, the table values shall be used without adjustments.

For SI units: 1 foot = 304.8 mm, 1000 British thermal units per hour = 0.293 kW

**FIGURE F 102.1COMMON VENTING TWO DRAFT HOOD-EQUIPPED APPLIANCESEXAMPLE 4**

In the common vent capacity portion of Table 803.2(2), find the row associated with a 30 foot (9144 mm) vent height and read over to the NAT + NAT portion of the 6 inch (152 mm) diameter column to find a maximum combined capacity of 257 000 Btu/h (75 kW). Since the two appliances total 185 000 Btu/h (54 kW), a 6 inch (152 mm) common vent shall be used.

### Related Code Sections

*VENTING*

*TWO*

*DRAFT*

*HOOD*-

*EQUIPPED*

*APPLIANCES*

*EXAMPLE*

*4*In the

*common*

*vent*capacity portion of Table 803.2(

*2*), find the row associated with a 30 foot (9144 ...

*COMMON*

*VENTING*

*TWO*

*DRAFT*

*HOOD*-

*EQUIPPED*

*APPLIANCES*—

*EXAMPLE*

*4*...

*VENT*SYSTEMS SERVING

*TWO*OR MORE

*DRAFT*

*HOOD*-

*EQUIPPED*

*APPLIANCES*

*Example*: Manifolded ...

*example*, 24 inches to 20 inches (610 mm to 508 mm) is a

*two*-size reduction]. The fan-assisted

*appliance*(s) is

*common*

*vented*with a

*draft*-

*hood*...