// CODE SNIPPET
E3905.12.2.5 Equipment Grounding Conductor Fill
JUMP TO FULL CODE CHAPTER
Related Code Sections
E3905.12.2.5 Power and Lighting Distribution, Equipment Grounding Conductor Fill
Where one or more equipment grounding conductors or equipment bonding jumpers enters a box, a single volume allowance in accordance with Table ...
2015 Michigan Residential Code > 39 Power and Lighting Distribution > E3905 Boxes, Conduit Bodies and Fittings > E3905.12 Number of Conductors in Outlet, Device, and Junction Boxes, and Conduit Bodies > E3905.12.2 Box Fill Calculations > E3905.12.2.5 Equipment Grounding Conductor Fill
Section E3908 Power and Lighting Distribution, Grounding
Metal enclosures of conductors, devices and equipment shall be connected to the equipment grounding conductor. (250.86) Exceptions : Short ...
Section E4205 Swimming Pools, Grounding
products listed for the application without a grounding conductor. All electrical equipment located within 5 feet (1524 mm) of the inside wall ...
E3407.2 General Requirements, Equipment Grounding Conductors
Equipment grounding conductors of sizes 6 AWG and smaller shall be identified by a continuous green color or a continuous green color with one ...
2015 Michigan Residential Code > 34 General Requirements > E3407 Conductor and Terminal Identification > E3407.2 Equipment Grounding Conductors
E3607.3.1 Services, Equipment Grounding Conductor
An equipment grounding conductor as described in Section E3908 shall be run with the supply conductors and connected to the building or structure ...
2015 Michigan Residential Code > 36 Services > E3607 System Grounding > E3607.3 Buildings or Structures Supplied by Feeder(s) or Branch Circuit(s) > E3607.3.1 Equipment Grounding Conductor