// CODE SNIPPET
909.20.4.2.1 Engineered Ventilation System
JUMP TO FULL CODE CHAPTER
Where a specially engineered system is used, the system shall exhaust a quantity of air equal to not less than 90 air changes per hour from any vestibule in the emergency operation mode and shall be sized to handle three vestibules simultaneously. Smoke detectors shall be located at the floor-side entrance to each vestibule and shall activate the system for the affected vestibule. Smoke detectors shall be installed in accordance with Section 907.3.
Related Code Sections
909.20.4.2.1 Fire Protection and Life Safety Systems, Engineered Ventilation System
Where a specially engineered system is used, the system shall exhaust a quantity of air equal to not less than 90 air changes per hour from any ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 909 Smoke Control Systems > 909.20 Smokeproof Enclosures > 909.20.4 Mechanical Ventilation Alternative > 909.20.4.2 Vestibule Ventilation > 909.20.4.2.1 Engineered Ventilation System
(3) Special Equipment, Engineered Systems
system, the minimum ventilation requirements shall be permitted to be determined in accordance with calculations specified in the engineering study ...
National Electrical Code 2017 of Illinois > 6 Special Equipment > 625 Electric Vehicle Charging System > 625.52 Ventilation > (B) Ventilation Required > (3) Engineered Systems
4188.8.131.52 Special Detailed Requirements Based on Occupancy and Use, Fail-Safe Engineered Systems
Standby power for mechanical ventilation, treatment systems and temperature control systems shall not be required where an approved fail-safe ...
Building Code 2018 of Illinois > 4 Special Detailed Requirements Based on Occupancy and Use > 414 Hazardous Materials > 414.5 Inside Storage, Dispensing and Use > 414.5.2 Emergency or Standby Power > 4184.108.40.206 Fail-Safe Engineered Systems
(A) Special Conditions, Ventilation
ventilation in accordance with the manufacturer's recommendations and listing for the system. Informational Note No. 1: See NFPA 1-2015, Fire Code ...
National Electrical Code 2017 of Illinois > 7 Special Conditions > 706 Energy Storage Systems > 706.10 Energy Storage System Locations > (A) Ventilation
(A) Special Occupancies, Equipment for Delayed Automatic Connection
, and exhaust ventilating systems for airborne infectious/isolation rooms, protective environment rooms, exhaust fans for laboratory fume hoods, nuclear ...
National Electrical Code 2017 of Illinois > 5 Special Occupancies > 517 Health Care Facilities > 517.35 Equipment Branch Connection to Alternate Power Source > (A) Equipment for Delayed Automatic Connection