// CODE SNIPPET
E3404.9 Energized Parts Guarded Against Accidental Contact
Related Code Sections
E3404.9 General Requirements, Energized Parts Guarded Against Accidental Contact
Approved enclosures shall guard energized parts that are operating at 50 volts or more against accidental contact. [110.27(A)] ...
Residential Code 2018 of Kansas > 34 General Requirements > E3404 General Equipment Requirements > E3404.9 Energized Parts Guarded Against Accidental Contact
(B) Equipment for General Use, Accidental Contact
into accidental contact or bring conducting materials into accidental contact with exposed energized parts, terminals, or buses associated with them ...
National Electrical Code 2017 of Kansas > 4 Equipment for General Use > 460 Capacitors > 460.2 Enclosing and Guarding > (B) Accidental Contact
230.62 Wiring and Protection, Service Equipment — Enclosed or Guarded
Energized parts of service equipment shall be enclosed as specified in 230.62(A) or guarded as specified in 230.62(B ...
National Electrical Code 2017 of Kansas > 2 Wiring and Protection > 230 Services > 230.62 Service Equipment — Enclosed or Guarded
450.8 Equipment for General Use, Guarding
enclosure if accessible to qualified persons only. All energized parts shall be guarded in accordance with 110.27 and 110.34 ...
National Electrical Code 2017 of Kansas > 4 Equipment for General Use > 450 Transformers and Transformer Vaults (Including Secondary Ties) > 450.8 Guarding
110.56 General, Energized Parts
Bare terminals of transformers, switches, motor controllers, and other equipment shall be enclosed to prevent accidental contact with energized parts ...
National Electrical Code 2017 of Kansas > 1 General > 110 Requirements for Electrical Installations > 110.56 Energized Parts