// CODE SNIPPET
110.56 Energized Parts
Related Code Sections
110.56 General, Energized Parts
Bare terminals of transformers, switches, motor controllers, and other equipment shall be enclosed to prevent accidental contact with energized parts ...
National Electrical Code 2020 of Minnesota > 1 General > 110 Requirements for Electrical Installations > 110.56 Energized Parts
(D) Wiring and Protection, No Energized Parts
Plug fuses, fuseholders, and adapters shall have no exposed energized parts after fuses or fuses and adapters have been installed ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 240 Overcurrent Protection > 240.50 General > (D) No Energized Parts
(C) Equipment for General Use, Exposed Energized Parts
to be installed in the transformer enclosure if accessible to qualified persons only. All energized parts shall be guarded in accordance with 110.27 ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 450 Transformers and Transformer Vaults (Including Secondary Ties) > 450.8 Guarding > (C) Exposed Energized Parts
490.35 Equipment for General Use, Accessibility of Energized Parts
Doors that would provide unqualified persons access to high-voltage energized parts shall be locked. Permanent signs in accordance with 110.21(B ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 490 Equipment Over 1000 Volts, Nominal > 490.35 Accessibility of Energized Parts