// CODE SNIPPET
F 501.7 Enclosure Components
JUMP TO FULL CODE CHAPTER
The exterior fire department connection panel shall contain the necessary gauges, isolation valves, pressure-relief valves, pressure-regulating valves, check valves, tubing, fittings, supports, connectors, adapters, and other necessary components as required to allow the fire department's mobile air unit to connect and augment the system with a constant source of breathing air. Each fire department connection panel shall contain not less than two inlet air connections.
Related Code Sections
F 501.7 Firefighter Breathing Air Replenishment Systems, Enclosure Components
valves, check valves, tubing, fittings, supports, connectors, adapters, and other necessary components as required to allow the fire department's mobile ...
2018 Uniform Plumbing Code of Nevada > F Firefighter Breathing Air Replenishment Systems > F 501.0 Exterior Fire Department Connection Panel and Enclosure > F 501.7 Enclosure Components
510.3.6.1 Exhaust Systems, Within an Enclosure
Where openings are located in ducts within an enclosure, the access panel including its components shall be of the same fire rating as the enclosure ...
2018 Uniform Mechanical Code of Nevada > 5 Exhaust Systems > 510.0 Exhaust Duct Systems > 510.3 Openings > 510.3.6 Access Panels > 510.3.6.1 Within an Enclosure
665.20 Special Equipment, Enclosures
The converting device (excluding the component interconnections) shall be completely contained within an enclosure(s) of noncombustible material ...
National Electrical Code 2017 of Nevada > 6 Special Equipment > 665 Induction and Dielectric Heating Equipment > 665.20 Enclosures
(A) Special Conditions, Identification
as a component of an emergency circuit or system. Where boxes or enclosures are not encountered, exposed cable or raceway systems shall be permanently ...
National Electrical Code 2017 of Nevada > 7 Special Conditions > 700 Emergency Systems > 700.10 Wiring, Emergency System > (A) Identification
409.106 Equipment for General Use, Spacings
or accessible non-current-carrying metal parts, between uninsulated live parts of components and the enclosure, and at field wiring terminals shall ...
National Electrical Code 2017 of Nevada > 4 Equipment for General Use > 409 Industrial Control Panels > 409.106 Spacings