// CODE SNIPPET
184.108.40.206.2 Emergency Shutdown
JUMP TO FULL CODE CHAPTER
For continuous spray application operations, one or more manual emergency system shutdown stations shall be installed to serve each spray area. When activated, the stations shall accomplish at least the functions listed in 220.127.116.11.1(1) and 18.104.22.168.1(3) through 22.214.171.124.1(5). At least one such station shall be within ready access of operating personnel. If access to this station is likely to involve exposure to danger, an additional station shall be located adjacent to an exit from the area. [33:9.2.2]
Related Code Sections
126.96.36.199.2 Spraying, Dipping, and Coating Using Flammable or Combustible Materials, Emergency Shutdown
For continuous spray application operations, one or more manual emergency system shutdown stations shall be installed to serve each spray area. When ...
Fire Code 2018 of West Virginia > 43 Spraying, Dipping, and Coating Using Flammable or Combustible Materials > 43.1 Application > 43.1.7 Protection > 188.8.131.52 Continuous Spray Application Operations > 184.108.40.206.2 Emergency Shutdown
413.8 Gas Piping Installations, Emergency Shutdown Control
An emergency shutdown device shall be located within 75 feet (22 860 mm) of, but not less than 25 feet (7620 mm) from, dispensers and shall also ...
Fuel Gas Code 2015 of West Virginia > 4 Gas Piping Installations > 413 (IFGC) Compressed Natural Gas Motor Vehicle Fuel-Dispensing Facilities > 413.8 Emergency Shutdown Control
220.127.116.11 Flammable and Combustible Liquids, Emergency Shutdown Systems
Emergency shutdown systems shall be designed to fail to a safe position in the event of loss of normal system power (i.e., air or electric ...
Fire Code 2018 of West Virginia > 66 Flammable and Combustible Liquids > 66.19 Specific Operations > 66.19.5 Vapor Recovery and Vapor Processing Systems > 18.104.22.168 Emergency Shutdown Systems
22.214.171.124 Flammable and Combustible Liquids,
system, it shall be designed to ensure the line is not subjected to damage from pressure surges. Emergency shutdown systems shall be permitted ...
Fire Code 2018 of West Virginia > 66 Flammable and Combustible Liquids > 66.29 Wharves > 66.29.3 General Requirements > 126.96.36.199
188.8.131.52 Liquefied Petroleum Gases and Liquefied Natural Gases,
Emergency remote shutdown stations shall be identified by a sign, visible from the point of transfer, incorporating the words "Propane — Container ...
Fire Code 2018 of West Virginia > 69 Liquefied Petroleum Gases and Liquefied Natural Gases > 69.3 Installation of LP-gas Systems > 69.3.9 Internal Valves > 184.108.40.206