// CODE SNIPPET
Section 411 Emergency Showers and Eyewash Stations
JUMP TO FULL CODE CHAPTER
Emergency showers and eyewash stations shall conform to ISEA Z358.1.
Waste connections shall not be required for emergency showers and eyewash stations.
Where hot and cold water is supplied to an emergency shower or eyewash station, the temperature of the water supply shall only be controlled by a temperature actuated mixing valve complying with ASSE 1071.