// CODE SNIPPET
G.5.4 Emergency Gas Shutoff
JUMP TO FULL CODE CHAPTER
An emergency gas shutoff valve shall be provided on the gas supply outside of any room containing an appliance utilizing gas at a pressure at or above 15 psig (103 kPa gauge). The emergency shutoff valve shall be controlled from a break glass station located outside the room served and from the gas detection system monitoring the room. The emergency shutoff valve shall automatically stop the gas flow to the room(s) containing the appliance(s) in the event of an unsafe condition. The emergency shutoff valve shall be manually operable. Emergency gas shutoff valve bypasses shall be prohibited.
Related Code Sections
G.5.4 High Pressure Natural Gas Installations, Emergency Gas Shutoff
An emergency gas shutoff valve shall be provided on the gas supply outside of any room containing an appliance utilizing gas at a pressure ...
NYC Fuel Gas Code 2014 > G High Pressure Natural Gas Installations > G.5 Piping Requirements > G.5.4 Emergency Gas Shutoff
G.2.4.6 High Pressure Natural Gas Installations, Shutoff Valves Closure
The gas detection system alarm activation shall trigger emergency gas shutoff valves serving the affected area to close and stop the gas flow ...
NYC Fuel Gas Code 2014 > G High Pressure Natural Gas Installations > G.2 Construction Requirements > G.2.4 Gas Detection > G.2.4.6 Shutoff Valves Closure
E.6 Meters and Gas Service Piping, Outside Gas Cut-Off
Outside gas cut-off shall comply with the following: An outside gas service line valve or other outside emergency shutoff device or other means ...
§28-315.5.1 Maintenance of Buildings, Outside Gas Shut-Off
Existing gas services shall be provided with an outside emergency shutoff device acceptable to the commissioner and the fire commissioner ...
NYC General Admin. Provisions 2014 > 3 Maintenance of Buildings > 315 Retroactive Requirements > §28-315.5 Fuel Gas Systems > §28-315.5.1 Outside Gas Shut-Off
908.3.2 Fire Protection Systems, Shutoff of Gas Supply
The gas detection system shall automatically close the shutoff valve at the source on gas supply piping and tubing related to the system being ...
NYC Building Code 2014 > 9 Fire Protection Systems > 908 Emergency Alarm Systems > 908.3 Highly Toxic and Toxic Materials > 908.3.2 Shutoff of Gas Supply