18.104.22.168.3.3 Electrical Wiring, Equipment, Devices, and Components
All electrical wiring regulated by this code shall be permitted to be left in place, but removal or cleaning of exposed ends of the wiring to reveal clean or uncorroded surfaces is required. All electrical equipment, devices, and components of the electrical system of the building regulated by this code shall be removed and discarded. This shall include all smoke detectors.
- Electrical equipment, devices, or components in areas not exposed to the corrosive effects of defective drywall shall be permitted to be left in place or reused. Electrical equipment, devices, or components in areas exposed to the corrosive effects of defective drywall shall be cleaned, repaired, or replaced.
- Cord and plug connected appliances are not subject to this code and, therefore, cannot be required to be removed or replaced.
Note: All low voltage wiring associated with security systems, door bells, elevator controls, and other such components shall be removed and replaced or repaired.