// CODE SNIPPET
240.12 Electrical System Coordination
JUMP TO FULL CODE CHAPTER
Where an orderly shutdown is required to minimize the hazard(s) to personnel and equipment, a system of coordination based on the following two conditions shall be permitted:
Informational Note: The monitoring system may cause the condition to go to alarm, allowing corrective action or an orderly shutdown, thereby minimizing personnel hazard and equipment damage.
Related Code Sections
240.12 Wiring and Protection, Electrical System Coordination
Where an orderly shutdown is required to minimize the hazard(s) to personnel and equipment, a system of coordination based on the following two ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 240 Overcurrent Protection > 240.12 Electrical System Coordination
685.3 Special Equipment, Application of Other Articles
Protection of conductors 240.4 Electrical system coordination 240.12 Ground-fault protection of equipment 240.13(1) Grounding ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 685 Integrated Electrical Systems > 685.3 Application of Other Articles
(G) Special Occupancies, Coordination
Overcurrent protective devices serving the essential electrical system shall be coordinated for the period of time that a fault's duration extends ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 517 Health Care Facilities > 517.31 Requirements for the Essential Electrical System > (G) Coordination
(3) Special Equipment, Selective Coordination
of electrical systems. The selection shall be documented and made available to those authorized to design, install, maintain, and operate the system. Exception ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 695 Fire Pumps > 695.3 Power Source(s) for Electric Motor-Driven Fire Pumps > (C) Multibuilding Campus-Style Complexes > (3) Selective Coordination
645.27 Special Equipment, Selective Coordination
Critical operations data system(s) overcurrent protective devices shall be selectively coordinated with all supply-side overcurrent protective ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 645 Information Technology Equipment > 645.27 Selective Coordination