// CODE SNIPPET
1006.8 Electrical Requirements
JUMP TO FULL CODE CHAPTER
The power supply to the electrical control system shall be from a two-wire branch circuit that has a grounded conductor, or from an isolation transformer with a two-wire secondary. Where an isolation transformer is provided, one conductor of the secondary winding shall be grounded. Control voltage shall not exceed 150 volts nominal, line to line. Control and limit devices shall interrupt the ungrounded side of the circuit. A means of manually disconnecting the control circuit shall be provided and controls shall be arranged so that when deenergized, the burner shall be inoperative. Such disconnecting means shall be capable of being locked in the off position and shall be provided with ready access.
Related Code Sections
1006.8 Boilers, Water Heaters and Pressure Vessels, Electrical Requirements
The power supply to the electrical control system shall be from a two-wire branch circuit that has a grounded conductor, or from an isolation ...
2015 Michigan Mechanical Code > 10 Boilers, Water Heaters and Pressure Vessels > 1006 Safety and Pressure Relief Valves and Controls > 1006.8 Electrical Requirements
306.3.1 General Regulations, Electrical Requirements
A luminaire controlled by a switch located at the required passageway opening and a receptacle outlet shall be provided at or near the appliance ...
2015 Michigan Mechanical Code > 3 General Regulations > 306 Access and Service Space > 306.3 Appliances in Attics > 306.3.1 Electrical Requirements
M1305.1.3.1 General Mechanical System Requirements, Electrical Requirements
A luminaire controlled by a switch located at the required passageway opening and a receptacle outlet shall be installed at or near the appliance ...
2015 Michigan Residential Code > 13 General Mechanical System Requirements > M1305 Appliance Access > M1305.1 Appliance Access for Inspection Service, Repair and Replacement > M1305.1.3 Appliances in Attics > M1305.1.3.1 Electrical Requirements
AJ501.5.3 Existing Building and Structures, Additional Electrical Requirements
Where the work area includes any of the following areas within a dwelling unit, the requirements of Sections AJ501.5.3.1 through AJ501.5.3.5 shall ...
2015 Michigan Residential Code > J Existing Building and Structures > AJ501 Alterations > AJ501.5 Electrical Equipment and Wiring > AJ501.5.3 Additional Electrical Requirements
4184.108.40.206 Special Detailed Requirements Based on Use and Occupancy, Required Electrical Systems
in Section 2705.2.3.4 of the International Fire Code. Electrically operated systems required elsewhere in this code or in the International Fire Code ...
2015 Michigan Building Code > 4 Special Detailed Requirements Based on Use and Occupancy > 415 Groups H-1, H-2, H-3, H-4 and H-5 > 415.11 Group H-5 > 415.11.10 Emergency Power System > 4220.127.116.11 Required Electrical Systems