All newly installed electrical equipment and wiring relating to work done in any work area shall comply with all applicable requirements of NFPA 70 except as provided for in Section 808.3.
Existing wiring in all work areas in Group A-1, A-2, A-5, H and I occupancies shall be upgraded to meet the materials and methods requirements of Chapter 7.
All enclosed areas, other than closets, kitchens, basements, garages, hallways, laundry areas, utility areas, storage areas and bathrooms shall have a minimum of two duplex receptacle outlets or one duplex receptacle outlet and one ceiling or wall-type lighting outlet.
Kitchen areas shall have a minimum of two duplex receptacle outlets.
Laundry areas shall have a minimum of one duplex receptacle outlet located near the laundry equipment and installed on an independent circuit.
Newly installed receptacle outlets shall be provided with ground fault circuit interruption as required by NFPA 70.
At least one lighting outlet shall be provided in every bathroom, hallway, stairway, attached garage, and detached garage with electric power, and to illuminate outdoor entrances and exits.
At least one lighting outlet shall be provided in utility rooms and basements where such spaces are used for storage or contain equipment requiring service.
Clearance for electrical service equipment shall be provided in accordance with the NFPA 70.