R302.6 Dwelling-Garage Fire Separation
The garage shall be separated as required by Table R302.6. Openings in garage walls shall comply with Section R302.5. Attachment of gypsum board shall comply with Table R702.3.5. The wall separation provisions of Table R302.6 shall not apply to garage walls that are perpendicular to the adjacent dwelling unit wall.
|From the residence and attics||Not less than 1/2-inch gypsum board or equivalent applied to the|
|From habitable rooms above the garage||Not less than 5/8-inch Type X gypsum board or equivalent|
|Structure(s) supporting floor/ceiling assemblies used for separation|
required by this section
|Not less than 1/2-inch gypsum board or equivalent|
|Garages located less than 3 feet from a dwelling unit on the same lot||Not less than 1/2-inch gypsum board or equivalent applied to the interior|
side of exterior walls that are within this area
For SI: 1 inch = 25.4 mm, 1 foot = 304.8 mm.