// CODE SNIPPET
126.96.36.199.6 Duct Detector Installation
JUMP TO FULL CODE CHAPTER
Smoke detectors shall be installed, tested, and maintained in accordance with NFPA 72. [90A:188.8.131.52]
Where smoke detectors required by Section 6.4 of NFPA 90A are installed in a building not equipped with an approved fire alarm system as specified by 184.108.40.206.6.2, the following shall occur:
- Smoke detector activation required by Section 6.4 of NFPA 90A shall cause a visual and audible signal in a normally occupied area.
- Smoke detector trouble conditions shall be indicated visually or audibly in a normally occupied area and shall be identified as air duct detector trouble.
Related Code Sections
220.127.116.11.6 Fire Protection Systems, Duct Detector Installation
Smoke detectors shall be installed, tested, and maintained in accordance with NFPA 72 . [ 90A: 18.104.22.168 ...
Fire Code 2018 of West Virginia > 13 Fire Protection Systems > 13.7 Detection, Alarm, and Communications Systems > 13.7.4 Automatic Fire Detectors > 22.214.171.124 General Requirements > 126.96.36.199.6 Duct Detector Installation
2.2.d.3.B National Standards and Codes,
All heating, ventilation, air conditioning systems greater than 15,000 CFM shall have duct type smoke detectors installed in both supply and return ...
188.8.131.52 Features of Fire Protection, Smoke Detectors
actuates the damper. Approved smoke detector installations are located within the ducts in existing installations. [ 101 : 184.108.40.206.1 ...
Fire Code 2018 of West Virginia > 12 Features of Fire Protection > 12.9 Smoke Barriers > 12.9.5 Ducts and Air-Transfer Openings > 220.127.116.11 Smoke Detectors
607.3.3.2 Duct Systems, Smoke Damper Actuation
of the International Building Code and one of the following methods, as applicable: Where a smoke damper is installed within a duct, a smoke detector shall ...
Mechanical Code 2015 of West Virginia > 6 Duct Systems > 607 Duct and Transfer Openings > 607.3 Damper Testing, Ratings and Actuation > 607.3.3 Damper Actuation > 607.3.3.2 Smoke Damper Actuation
718.104.22.168 Fire and Smoke Protection Features, Smoke Damper Actuation
of the following methods, as applicable: Where a smoke damper is installed within a duct, a smoke detector shall be installed inside the duct or outside ...
Building Code 2015 of West Virginia > 7 Fire and Smoke Protection Features > 717 Ducts and Air Transfer Openings > 717.3 Damper Testing, Ratings and Actuation > 717.3.3 Damper Actuation > 722.214.171.124 Smoke Damper Actuation