// CODE SNIPPET
1310.2.2 Drops to Individual Stations
JUMP TO FULL CODE CHAPTER
Drops to individual station outlets and inlets shall be not less than DN15 (NPS 1/2) (5/8 inch O.D.) size. [NFPA 99:220.127.116.11.1.4]
|TYPE OF SYSTEM||MAXIMUM ALLOWABLE SYSTEM PRESSURE LOSS (psi)|
|Medical Vacuum||4 inches of mercury|
For SI units: 1 pound-force per square inch = 6.8947 kPa, 1 inch of mercury = 3.386 kPa
Related Code Sections
1310.2.2 Health Care Facilities and Medical Gas and Medical Vacuum Systems, Drops to Individual Stations
Drops to individual station outlets and inlets shall be not less than DN15 (NPS 1 / 2 ) ( 5 / 8 inch O.D.) size. [NFPA 99:18.104.22.168.1.4] TABLE ...
2018 Uniform Plumbing Code of Nevada > 13 Health Care Facilities and Medical Gas and Medical Vacuum Systems > 1310.0 Installation of Piping > 1310.2 Required Pipe Sizing > 1310.2.2 Drops to Individual Stations
(D) Special Equipment, Voltage Drop
The voltage drop on any branch circuit shall not exceed 1.5 percent. The combined voltage drop of feeder and branch-circuit conductors shall ...
National Electrical Code 2017 of Nevada > 6 Special Equipment > 647 Sensitive Electronic Equipment > 647.4 Wiring Methods > (D) Voltage Drop
695.7 Special Equipment, Voltage Drop
The voltage at the fire pump controller line terminals shall not drop more than 15 percent below normal (controller-rated voltage) under motor ...
8.4.1 Power, Voltage Drop
The feeder conductors and branch circuits combined shall be sized for a maximum of 5% voltage drop total ...
Energy Standard for Buildings Except Low-Rise Residential Buildings 2016 of Nevada > 8 Power > 8.4 Mandatory Provisions > 8.4.1 Voltage Drop
C 601.5 Alternate Plumbing Systems, Maximum Vertical Drops From Fixtures
Vertical drops from fixture traps to horizontal branch piping shall be one size larger than the trap size, but not less than 2 inches (50 mm ...
2018 Uniform Plumbing Code of Nevada > C Alternate Plumbing Systems > C 601.0 Single-Stack Vent System > C 601.5 Maximum Vertical Drops From Fixtures