// CODE SNIPPET
1301.9.8 Draining of Tanks
JUMP TO FULL CODE CHAPTER
Tanks shall be provided with a means of emptying the contents for the purpose of service or cleaning. Tanks shall be drained by using a pump or by a drain located at the lowest point in the tank. The tank drain pipe shall discharge as required for overflow pipes and shall not be smaller in size than specified in Table 606.5.7. Not less than one cleanout shall be provided on each drain pipe in accordance with Section 708.
Related Code Sections
1301.9.8 Nonpotable Water Systems, Draining of Tanks
Tanks shall be provided with a means of emptying the contents for the purpose of service or cleaning. Tanks shall be drained by using a pump ...
Plumbing Code 2018 of Kansas > 13 Nonpotable Water Systems > 1301 General > 1301.9 Nonpotable Water Storage Tanks > 1301.9.8 Draining of Tanks
606.5.7 Water Supply and Distribution, Tank Drain Pipes
A drain pipe with a valve shall be provided at the lowest point of each tank to permit emptying of the tank. The tank drain pipe shall discharge ...
Plumbing Code 2018 of Kansas > 6 Water Supply and Distribution > 606 Installation of the Building Water Distribution System > 606.5 Water Pressure Booster Systems > 606.5.7 Tank Drain Pipes
2405.3.2 Flammable Finishes, Bottom Drains
Dip tanks greater than 500 gallons (1893 L) in liquid capacity shall be equipped with bottom drains that are arranged to automatically and manually ...
Fire Code 2018 of Kansas > 24 Flammable Finishes > 2405 Dipping Operations > 2405.3 Construction of Dip Tanks > 2405.3.2 Bottom Drains
184.108.40.206 Electric Elevators,
Where permitted and provided, pipes, drains, and tanks, or similar equipment that contains liquids, shall not be located directly above the elevator ...
Safety Code for Elevators and Escalators 2016 of Kansas > 2 Electric Elevators > 2.8 Equipment in Hoistways, Machinery Spaces, Machine Rooms, Control Spaces, and Control Rooms > 2.8.3 Pipes, Ducts, Tanks, and Sprinklers > 220.127.116.11