// CODE SNIPPET
312.4 Drainage and Vent Final Test
JUMP TO FULL CODE CHAPTER
The final test of the completed drainage and vent systems shall be visual and in sufficient detail to determine compliance with the provisions of this code. Where a smoke test is utilized, it shall be made by filling all traps with water and then introducing into the entire system a pungent, thick smoke produced by one or more smoke machines. When the smoke appears at stack openings on the roof, the stack openings shall be closed and a pressure equivalent to a 1-inch water column (248.8 Pa) shall be held for a test period of not less than 15 minutes.
Related Code Sections
312.4 General Regulations, Drainage and Vent Final Test
The final test of the completed drainage and vent systems shall be visual and in sufficient detail to determine compliance with the provisions ...
Plumbing Code 2018 of Kansas > 3 General Regulations > 312 Tests and Inspections > 312.4 Drainage and Vent Final Test
P3009.3 Sanitary Drainage, Tests
Drain, waste and vent piping for subsurface landscape irrigation systems shall be tested in accordance with Section P2503 ...
Residential Code 2018 of Kansas > 30 Sanitary Drainage > P3009 Subsurface Landscape Irrigation Systems > P3009.3 Tests
R403.3.3 Foundations, Drainage
Final grade shall be sloped in accordance with Section R401.3. In other than Group I Soils, as detailed in Table R405.1, gravel or crushed stone ...
Residential Code 2018 of Kansas > 4 Foundations > R403 Footings > R403.3 Frost-Protected Shallow Foundations > R403.3.3 Drainage
P2503.5 Plumbing Administration, Drain, Waste and Vent Systems Testing
Rough-in and finished plumbing installations of drain, waste and vent systems shall be tested in accordance with Sections P2503.5.1 and P2503.5.2 ...
Residential Code 2018 of Kansas > 25 Plumbing Administration > P2503 Inspection and Tests > P2503.5 Drain, Waste and Vent Systems Testing
503.9 Chimneys and Vents, Condensation Drainage
Provisions shall be made to collect and dispose of condensate from venting systems serving Category II and IV appliances and noncategorized ...
Fuel Gas Code 2018 of Kansas > 5 Chimneys and Vents > 503 (IFGS) Venting of Appliances > 503.9 Condensation Drainage