Section 706 Dosing
The dosing frequency shall be not greater than four times daily. A volume per dose shall be established by dividing the daily wastewater flow by the dosing frequency. The dosing volume shall be not less than 10 times the capacity of the distribution pipe volume. Table 706.1 provides the estimated volume for various pipe diameters.
ESTIMATED VOLUME FOR VARIOUS DIAMETER PIPES
(gallons per foot length)
For SI: 1 inch = 25.4 mm, 1 gallon per foot = 0.012 L/mm.