// CODE SNIPPET
604.9.3.1 Door Opening Location
JUMP TO FULL CODE CHAPTER
The farthest edge of toilet compartment door opening shall be located in the front wall or partition or in the side wall or partition as required by Table 604.9.3.1.
DOOR OPENING LOCATION
|DOOR OPENING LOCATION||MEASURED FROM||DIMENSION|
|Front Wall or Partition||From the side wall or |
partition closet to the water closet
|56 inches (1420 mm) minimum|
|From the side wall or |
partition farthest from the water closet
|4 inches (100 mm) maximum|
|Side Wall or Partition |
Wall-Hung Water Closet
|From the rear wall||52 inches (1320 mm) minimum|
|From the front wall or partition||4 inches (100 mm) minimum|
|Side Wall or Partition |
Floor-Mounted Water Closet
|From the rear wall||55 inches (1395 mm) minimum|
|From the front wall or partition||4 inches (100 mm) maximum|
WHEELCHAIR ACCESSIBLE COMPARTMENT DOOR OPENINGS
WHEELCHAIR ACCESSIBLE COMPARTMENT DOOR OPENINGS—ALTERNATE
Related Code Sections
604.9.3.1 Plumbing Elements and Facilities, Door Opening Location
The farthest edge of toilet compartment door opening shall be located in the front wall or partition or in the side wall or partition as required ...
Minnesota Accessibility Code 2015 > 6 Plumbing Elements and Facilities > 604 Water Closets and Toilet Compartments > 604.9 Wheelchair Accessible Compartments > 604.9.3 Doors > 604.9.3.1 Door Opening Location
408.3.3 Accessible Routes, Door Location and Width
that provide an 18 square foot (1.67 m 2 ) platform. Doors located on the narrow end of cars shall provide a clear opening width of 36 inches (915 mm) minimum ...
Minnesota Accessibility Code 2015 > 4 Accessible Routes > 408 Limited-Use/Limited- Application Elevators > 408.3 Elevator Door Requirements > 408.3.3 Door Location and Width
703.3.11 Communication Elements and Features, Location
containing raised characters and braille is provided at double doors with one active leaf, the sign shall be located on the inactive leaf. Where a sign ...
Minnesota Accessibility Code 2015 > 7 Communication Elements and Features > 703 Signs > 703.3 Raised Characters > 703.3.11 Location
7188.8.131.52 Fire and Smoke Protection Features, Smoke-Activated Doors
Automatic-closing doors installed in the following locations shall be permitted to have hold-open devices. Doors shall automatically close ...
2020 Minnesota Building Code > 7 Fire and Smoke Protection Features > 716 Opening Protectives > 716.2 Fire Door Assemblies > 716.2.6 Fire Door Hardware and Closures > 7184.108.40.206 Smoke-Activated Doors
3113.1.1 Special Construction, Roof Access Points
Roof access points shall be located in areas that do not require the placement of fire department ground ladders over openings such as windows ...
Minnesota Building Code 2015 > 31 Special Construction > 3113 Solar Photovoltaic Power Systems > 3113.1 Access and Pathways > 3113.1.1 Roof Access Points