G2439.7 (614.8) Domestic Clothes Dryer Exhaust Ducts
The maximum length of the exhaust duct shall be 35 feet (10 668 mm) from the connection to the transition duct from the dryer to the outlet terminal. Where fittings are used, the maximum length of the exhaust duct shall be reduced in accordance with Table G2418.104.22.168.
TABLE G2422.214.171.124 (TABLE 6126.96.36.199)
|DRYER EXHAUST DUCT FITTING TYPE||EQUIVALENT LENGTH|
|4-inch radius mitered 45-degree elbow||2 feet, 6 inches|
|4-inch radius mitered 90-degree elbow||5 feet|
|6-inch radius smooth 45-degree elbow||1 foot|
|6-inch radius smooth 90-degree elbow||1 foot, 9 inches|
|8-inch radius smooth 45-degree elbow||1 foot|
|8-inch radius smooth 90-degree elbow||1 foot, 7 inches|
|10-inch radius smooth 45-degree elbow||9 inches|
|10-inch radius smooth 90-degree elbow||1 foot, 6 inches|
For SI: 1 inch = 25.4 mm, 1 foot = 304.8 mm, 1 degree = 0.0175 rad.
Where space for a clothes dryer is provided, an exhaust duct system shall be installed.
Where the clothes dryer is not installed at the time of occupancy, the exhaust duct shall be capped at the location of the future dryer.
Exception: Where a listed condensing clothes dryer is installed prior to occupancy of the structure.