// CODE SNIPPET
904.8 Distribution System
JUMP TO FULL CODE CHAPTER
Distribution systems shall be placed on the aggregate, with the holes located on the bottom of the distribution pipe. The ends of all distribution pipes shall be marked at the surface, and an observation pipe shall be placed to the bottom of the bed or each trench.
Related Code Sections
904.8 Mound Systems, Distribution System
Distribution systems shall be placed on the aggregate, with the holes located on the bottom of the distribution pipe. The ends of all distribution ...
Private Sewage Disposal Code 2018 of Puerto Rico > 9 Mound Systems > 904 Construction Techniques > 904.8 Distribution System
Chapter 7 Pressure Distribution Systems
308.9 General Regulations, Parallel Water Distribution Systems
Piping bundles for manifold systems shall be supported in accordance with Table 308.5. Support at changes in direction shall be in accordance ...
Plumbing Code 2018 of Puerto Rico > 3 General Regulations > 308 Piping Support > 308.9 Parallel Water Distribution Systems
Appendix B Tables for Pressure Distribution Systems
, distribution discharge rate and hole diameter of pressure distribution systems by the placement of a straightedge between two known points ...
Section P2905 Water Supply and Distribution, Heated Water Distribution Systems
Circulation systems and heat trace systems that are installed to bring heated water in close proximity to one or more fixtures shall meet ...
Residential Code 2018 of Puerto Rico > 29 Water Supply and Distribution > P2905 Heated Water Distribution Systems