// CODE SNIPPET
1910.107(b)(4) Distribution or Baffle Plates
JUMP TO FULL CODE CHAPTER
Distribution or baffle plates, if installed to promote an even flow of air through the booth or cause the deposit of overspray before it enters the exhaust duct, shall be of noncombustible material and readily removable or accessible on both sides for cleaning. Such plates shall not be located in exhaust ducts.