// CODE SNIPPET
6304.1.2 Distance From Detached Storage Buildings to Exposures
JUMP TO FULL CODE CHAPTER
In addition to the requirements of the International Building Code, detached storage buildings shall be located in accordance with Table 6304.1.2.
|MINIMUM DISTANCE TO BUILDINGS,
LOT LINES, PUBLIC STREETS, PUBLIC
ALLEYS, PUBLIC WAYS OR MEANS OF
|1||Note a||Not Required|
|4||Over 10 to 100||75|
|101 to 500||100|
|501 to 1,000||125|
|1,001 to 3,000||200|
|3,001 to 5,000||300|
|5,001 to 10,000||400|
|Over 10,000||As required by the fire code official|
Related Code Sections
6304.1.2 Oxidizers, Oxidizing Gases and Oxidizing Cryogenic Fluids, Distance From Detached Storage Buildings to Exposures
TABLE 6304.1.2 OXIDIZER LIQUIDS AND SOLIDS—DISTANCE FROM DETACHED BUILDINGS AND OUTDOOR STORAGE AREAS TO EXPOSURES OXIDIZER CLASS ...
Fire Code 2012 of Tennessee > 63 Oxidizers, Oxidizing Gases and Oxidizing Cryogenic Fluids > 6304 Storage > 6304.1 Indoor Storage > 6304.1.2 Distance From Detached Storage Buildings to Exposures
6204.1.2 Organic Peroxides, Distance From Detached Buildings to Exposures
DETACHED STORAGE BUILDINGS OR OUTDOOR STORAGE AREAS ORGANIC PEROXIDE CLASS MAXIMUM STORAGE QUANTITY (POUNDS) AT MINIMUM SEPARATION DISTANCE ...
Fire Code 2012 of Tennessee > 62 Organic Peroxides > 6204 Storage > 6204.1 Indoor Storage > 6204.1.2 Distance From Detached Buildings to Exposures
5904.2.1 Flammable Solids, Distance From Storage to Exposures
of the storage area is allowed in lieu of such distance. The wall shall either be an independent structure, or the exterior wall of the building adjacent ...
Fire Code 2012 of Tennessee > 59 Flammable Solids > 5904 Storage > 5904.2 Outdoor Storage > 5904.2.1 Distance From Storage to Exposures
5404.2.2 Corrosive Materials, Distance From Storage to Exposures
Outdoor storage of corrosive materials shall not be within 20 feet (6096 mm) of buildings not associated with the manufacturing or distribution ...
Fire Code 2012 of Tennessee > 54 Corrosive Materials > 5404 Storage > 5404.2 Outdoor Storage > 5404.2.2 Distance From Storage to Exposures