// CODE SNIPPET
[F] 415.5.2 Dispensing, Use and Handling
JUMP TO FULL CODE CHAPTER
Where hazardous materials having a hazard ranking of 3 or 4 in accordance with NFPA 704 are transported through corridors, interior exit stairways or ramps, or exit passageways, there shall be an emergency telephone system, a local manual alarm station or an approved alarm-initiating device at not more than 150-foot (45 720 mm) intervals and at each exit and exit access doorway throughout the transport route. The signal shall be relayed to an approved central, proprietary or remote station service or constantly attended on-site location and shall initiate a local audible alarm.
Related Code Sections
415.5.2 Special Detailed Requirements Based on Occupancy and Use, Dispensing, Use and Handling
Where hazardous materials having a hazard ranking of 3 or 4 in accordance with NFPA 704 are transported through corridors, interior exit stairways ...
Building Code 2018 of Illinois > 4 Special Detailed Requirements Based on Occupancy and Use > 415 Groups H-1, H-2, H-3, H-4 and H-5 > 415.5 Emergency Alarms > 415.5.2 Dispensing, Use and Handling
(2) Special Occupancies, Alcohol-Based Windshield Washer Fluid
The area used for storage, handling, or dispensing into motor vehicles of alcohol-based windshield washer fluid in repair garages shall ...
National Electrical Code 2017 of Illinois > 5 Special Occupancies > 511 Commercial Garages, Repair and Storage > 511.3 Area Classification, General > (E) Modifications to Classification > (2) Alcohol-Based Windshield Washer Fluid
604.9.6 Plumbing Elements and Facilities, Dispensers
Toilet paper dispensers shall comply with 309.4 and shall be 7 inches (180 mm) minimum and 9 inches (230 mm) maximum in front of the water closet ...
2018 Illinois Accessibility Code > 6 Plumbing Elements and Facilities > 604 Water Closets and Toilet Compartments > 604.9 Water Closets and Toilet Compartments for Children's Use > 604.9.6 Dispensers
(3) Special Occupancies, Handle
The handle of the spraying gun shall be electrically connected to ground by a conductive material and be constructed so that the operator in normal ...
National Electrical Code 2017 of Illinois > 5 Special Occupancies > 516 Spray Application, Dipping, Coating, and Printing Processes Using Flammable or Combustible Materials > 516.10 Special Equipment > (B) Hand-Spraying Electrostatic Equipment > (3) Handle
(1) Special Occupancies, Class I Locations
Table 514.3(B)(1) shall be applied where Class I liquids are stored, handled, or dispensed and shall be used to delineate and classify motor fuel ...
National Electrical Code 2017 of Illinois > 5 Special Occupancies > 514 Motor Fuel Dispensing Facilities > 514.3 Classification of Locations > (B) Classified Locations > (1) Class I Locations