445.18 Disconnecting Means and Shutdown of Prime Mover
- Be equipped with provisions to disable all prime mover start control circuits to render the prime mover incapable of starting
- Initiate a shutdown mechanism that requires a mechanical reset
Generators with greater than 15 kW rating shall be provided with an additional requirement to shut down the prime mover. This additional shutdown means shall be located outside the equipment room or generator enclosure and shall also meet the requirements of 445.18(B)(1) and (B)(2).