// CODE SNIPPET
P-1202.2 Discharge of Indirect Waste
JUMP TO FULL CODE CHAPTER
Indirect waste pipes shall discharge into and above the flood level of a trapped open sink or approved receptacle, properly supplied with water, which shall be vented where required by this code and which shall be located in an accessible ventilated place. An air gap shall exist between the outlet end of the waste pipe and the flood-level rim of the receiving sink or approved receptacle. The air gap in each instance shall be at least twice the diameter of the indirect waste pipe. If the indirect waste has sufficient year-round flow to maintain the trap seal, the sink or receptacle need not be supplied with water. The area of the receptor drain line shall be equal to or greater than the total area of all lines discharging into it. The size of the receptor drain line shall be a minimum of 2- inches and the receptor shall be of such size as to prevent overflowing of the receptor, but in no case shall it be less than 2".
Related Code Sections
P-1202.2 Indirect and Special Waste, Discharge of Indirect Waste
Indirect waste pipes shall discharge into and above the flood level of a trapped open sink or approved receptacle, properly supplied with water ...
Philadelphia Plumbing Code > 12 Indirect and Special Waste > P-1202 Indirect Waste Pipes > P-1202.2 Discharge of Indirect Waste
P-706.7.1 Plumbing Fixtures, Drains
The drain for the water supply shall spill on grade, discharge to an independent seepage pit, or discharge to indirect waste in accordance ...
Philadelphia Plumbing Code > 7 Plumbing Fixtures > P-706 Water Closets > P-706.7 Frost-Proof Closets > P-706.7.1 Drains
802.4.1 Indirect/Special Waste, Size of Receptors
A waste receptor shall be sized for the maximum discharge of all indirect waste pipes served by the receptor. Receptors shall be installed to prevent ...
Plumbing Code 2018 of Philadelphia > 8 Indirect/Special Waste > 802 Indirect Wastes > 802.4 Waste Receptors > 802.4.1 Size of Receptors
Section P-807 Water Supply and Distribution, Pumps, Wells, and Other Appliances
, discharge to independent seepage pit, or discharge to indirect waste in accordance with Section P-1201.2 ...
Philadelphia Plumbing Code > 8 Water Supply and Distribution > P-807 Pumps, Wells, and Other Appliances