// CODE SNIPPET

# 1113.5 Discharge Capacity

JUMP TO FULL CODE CHAPTER
The minimum required discharge capacity of the pressure-relief device or fusible plug
for a pressure vessel shall be determined in accordance with
Equation 1113.5:

Where:

Where combustible materials are used within 20 ft (6096 mm) of a pressure vessel, the value off shall be multiply by 2.5. Equation 1113.5 is based on fire conditions, other heat sources shall be calculated separately. Where one pressure-relief device or fusible plug is used to protect more than one pressure vessel, the required capacity shall be the sum of the capacity required for every pressure vessel. [ASHRAE 15:9.7.5]

*C = fDL*(Equation 1113.5)

Where:

C |
= | Minimum required discharge capacity of the relief device expressed as mass flow of air, pounds per minute (kg/s). |

D |
= | Outside diameter of vessel, feet (m). |

L |
= | Length of vessel, feet (m). |

f |
= | Factor dependent upon type of refrigerant from Table 1113.5. |

Where combustible materials are used within 20 ft (6096 mm) of a pressure vessel, the value off shall be multiply by 2.5. Equation 1113.5 is based on fire conditions, other heat sources shall be calculated separately. Where one pressure-relief device or fusible plug is used to protect more than one pressure vessel, the required capacity shall be the sum of the capacity required for every pressure vessel. [ASHRAE 15:9.7.5]

REFRIGERANT |
VALUE OF f |

Where used on the lowside of a limited-charge cascade system: | |

R-23, R-170, R-744, R-1150, R-508A, R-508B | 1 |

R-13, R-13B1, R-503 | 2 |

R-14 | 2.5 |

Other applications: | |

R-718 | 0.2 |

R-717 | 0.5 |

R-11, R-32, R-113, R-123, R-142b, R-152a, R-290, R-600, R-600a, R-764 |
1 |

R-12, R-22, R-114, R-124, R-134a, R-401A, R-401B, R-401C, R- 405A, R-406A, R-407C, R-407D, R-407E, R-409A, R-409B, R- 411A, R-411B, R-411C, R-412A, R-414A, R-414B, R-500, R-1270 |
1.6 |

R-143a, R-402B, R-403A, R-407A, R408A, R-413A | 2 |

R-115, R-402A, R-403B, R-404A, R-407B, R-410A, R-410B, R- 502, R-507A, R-509A |
2.5 |

### Related Code Sections

1113.5 Refrigeration, Discharge Capacity

The minimum required

*discharge**capacity*of the pressure-relief device or fusible plug for a pressure vessel shall be determined in accordance ...
Los Angeles Mechanical Code > 11 Refrigeration > 1113.0 Overpressure Protection > 1113.5 Discharge Capacity

1113.5 Refrigeration, Discharge Capacity

The minimum required

*discharge**capacity*of the pressure-relief device or fusible plug for a pressure vessel shall be determined in accordance ...
Los Angeles Mechanical Code > 11 Refrigeration > 1113.0 Overpressure Protection > 1113.5 Discharge Capacity

1028.2 Means of Egress, Exit Discharge Width or Capacity

The minimum width or required

*capacity*of the exit*discharge*shall be not less than the minimum width or required*capacity*of the exits being served ...
2017 LA City Fire Code > 10 Means of Egress > 1028 Exit Discharge > 1028.2 Exit Discharge Width or Capacity

1028.2 Means of Egress, Exit Discharge Width or Capacity

The minimum width or required

*capacity*of the exit*discharge*shall be not less than the minimum width or required*capacity*of the exits being served ...
Los Angeles Building Code > 10 Means of Egress > 1028 Exit Discharge > 1028.2 Exit Discharge Width or Capacity

1028.2 Means of Egress, Exit Discharge Width or Capacity

The minimum width or required

*capacity*of the exit*discharge*shall be not less than the minimum width or required*capacity*of the exits being ...
Los Angeles Building Code > 10 Means of Egress > 1028 Exit Discharge > 1028.2 Exit Discharge Width or Capacity