// CODE SNIPPET
E3905.12.2.4 Device or Equipment Fill
JUMP TO FULL CODE CHAPTER
For each yoke or strap containing one or more devices or equipment, a double volume allowance in accordance with Table E3905.12.2.1 shall be made for each yoke or strap based on the largest conductor connected to a device(s) or equipment supported by that yoke or strap. For a device or utilization equipment that is wider than a single 2-inch (51 mm) device box as described in Table E3905.12.1, a double volume allowance shall be made for each ganged portion required for mounting of the device or equipment. [314.16(B)(4)]
Related Code Sections
E3905.12.2.4 Power and Lighting Distribution, Device or Equipment Fill
For each yoke or strap containing one or more devices or equipment, a double volume allowance in accordance with Table E3905.12.2.1 shall be made ...
2015 Michigan Residential Code > 39 Power and Lighting Distribution > E3905 Boxes, Conduit Bodies and Fittings > E3905.12 Number of Conductors in Outlet, Device, and Junction Boxes, and Conduit Bodies > E3905.12.2 Box Fill Calculations > E3905.12.2.4 Device or Equipment Fill
425.3 Fixtures, Faucets and Fixture Fittings, Flush Tanks
Flush tanks equipped for manual flushing shall be controlled by a device designed to refill the tank after each discharge and to shut off completely ...
2015 Michigan Plumbing Code > 4 Fixtures, Faucets and Fixture Fittings > 425 Flushing Devices for Water Closets and Urinals > 425.3 Flush Tanks
Section 1306 Fuel Oil Piping and Storage, Oil Gauging
provided with fill and vent pipes shall be provided with a device to indicate either visually or audibly at the fill point when the oil in the tank has ...
P2712.3 Plumbing Fixtures, Water Supply for Flushing Devices
An adequate quantity of water shall be provided to flush and clean the fixture served. The water supply to flushing devices equipped for manual ...
2015 Michigan Residential Code > 27 Plumbing Fixtures > P2712 Water Closets > P2712.3 Water Supply for Flushing Devices
307.2.3 General Regulations, Auxiliary and Secondary Drain Systems
be equipped with a water-level detection device conforming to UL 508 that will shut off the equipment served prior to overflow of the pan. The ...
2015 Michigan Mechanical Code > 3 General Regulations > 307 Condensate Disposal > 307.2 Evaporators and Cooling Coils > 307.2.3 Auxiliary and Secondary Drain Systems