// CODE SNIPPET
5001.3.3.8 Detection of Gas or Vapor Release
Related Code Sections
5001.3.3.8 Hazardous Materials—General Provisions, Detection of Gas or Vapor Release
Where a release of hazardous materials gas or vapor would cause immediate harm to persons or property, means of mitigating the dangerous effects ...
Los Angeles Fire Code > 50 Hazardous Materials—General Provisions > 5001 General > 5001.3 Performance-Based Design Alternative > 5001.3.3 Performance Requirements > 5001.3.3.8 Detection of Gas or Vapor Release
5303.16.10 Compressed Gases, Monitoring and Detection
Vaults shall be provided with approved vapor and liquid detection systems and equipped with on-site audible and visual warning devices with battery ...
Los Angeles Fire Code > 53 Compressed Gases > 5303 General Requirements > 5303.16 Vaults > 5303.16.10 Monitoring and Detection
1406.3.3 Process Piping, Gas-Detection System
the accepted permissible exposure limit for the gas, a continuous gas-monitoring system shall be provided to detect the presence of a short-term hazard ...
Los Angeles Mechanical Code > 14 Process Piping > 1406.0 Pipe, Tubing, and Fittings > 1406.3 Special Requirements for HPP Gases > 1406.3.3 Gas-Detection System
6004.2.2 Highly Toxic and Toxic Materials, General Indoor Requirements
treatment system shall be utilized to handle the accidental release of gas and to process exhaust ventilation. The treatment system shall be designed ...
Los Angeles Fire Code > 60 Highly Toxic and Toxic Materials > 6004 Highly Toxic and Toxic Compressed Gases > 6004.2 Indoor Storage and Use > 6004.2.2 General Indoor Requirements
415.11.7 Special Detailed Requirements Based on Use and Occupancy, Gas Detection Systems
A gas detection system complying with Section 916 shall be provided for HPM gases where the physiological warning threshold level of the gas ...
Los Angeles Building Code > 4 Special Detailed Requirements Based on Use and Occupancy > 415 Groups H-1, H-2, H-3, H-4 and H-5 > 415.11 Group H-5 > 415.11.7 Gas Detection Systems