// CODE SNIPPET
510.3 Design and Operation
Related Code Sections
510.3 Exhaust Systems, Design and Operation
The design and operation of the exhaust system shall be such that flammable contaminants are diluted in noncontaminated air to maintain ...
2015 Michigan Mechanical Code > 5 Exhaust Systems > 510 Hazardous Exhaust Systems > 510.3 Design and Operation
G2413.6 Fuel Gas, (402.6) Maximum Design Operating Pressure
The maximum design operating pressure for piping systems located inside buildings shall not exceed 5 pounds per square inch gauge (psig) (34 kPa ...
2015 Michigan Residential Code > 24 Fuel Gas > G2413 (402) Pipe Sizing > G2413.6 (402.6) Maximum Design Operating Pressure
4220.127.116.11 Special Detailed Requirements Based on Use and Occupancy, Exhaust Ventilation Systems
Exhaust ventilation systems are allowed to be designed to operate at not less than one-half the normal fan speed on the emergency power system ...
2015 Michigan Building Code > 4 Special Detailed Requirements Based on Use and Occupancy > 415 Groups H-1, H-2, H-3, H-4 and H-5 > 415.11 Group H-5 > 415.11.10 Emergency Power System > 418.104.22.168 Exhaust Ventilation Systems
G2417.3.3 Fuel Gas, (406.3.3) Appliance and Equipment Disconnection
Where the piping system is connected to appliances or equipment designed for operating pressures of less than the test pressure ...
2015 Michigan Residential Code > 24 Fuel Gas > G2417 (406) Inspection, Testing and Purging > G2417.3 (406.3) Test Preparation > G2417.3.3 (406.3.3) Appliance and Equipment Disconnection
502.8.2 Exhaust Systems, Gas Rooms, Exhausted Enclosures and Gas Cabinets
The ventilation system for gas rooms, exhausted enclosures and gas cabinets for any quantity of hazardous material shall be designed to operate ...
2015 Michigan Mechanical Code > 5 Exhaust Systems > 502 Required Systems > 502.8 Hazardous Materials-General Requirements > 502.8.2 Gas Rooms, Exhausted Enclosures and Gas Cabinets