// CODE SNIPPET
1910.106(d)(4) Design and Construction of Inside Storage Rooms
Go To Full Code Chapter
Inside storage rooms shall be constructed to meet the required fire-resistive rating for their use. Such construction shall comply with the test specifications set forth in Standard Methods of Fire Tests of Building Construction and Materials, NFPA 251-1969. Where an automatic sprinkler system is provided, the system shall be designed and installed in an acceptable manner. Openings to other rooms or buildings shall be provided with noncombustible liquid-tight raised sills or ramps at least 4 inches in height, or the floor in the storage area shall be at least 4 inches below the surrounding floor. Openings shall be provided with approved self-closing fire doors. The room shall be liquid-tight where the walls join the floor. A permissible alternate to the sill or ramp is an open-grated trench inside of the room which drains to a safe location. Where other portions of the building or other properties are exposed, windows shall be protected as set forth in the Standard for Fire Doors and Windows, NFPA No. 80-1968, which is incorporated by reference as specified in Sec. 1910.6, for Class E or F openings. Wood at least 1 inch nominal thickness may be used for shelving, racks, dunnage, scuffboards, floor overlay, and similar installations.
Electrical wiring and equipment located in inside storage rooms used for Category 1 or 2 flammable liquids, or Category 3 flammable liquids with a flashpoint below 100 °F (37.8 °C), shall be approved under subpart S of this part for Class I, Division 2 Hazardous Locations; for Category 3 flammable liquids with a flashpoint at or above 100 °F (37.8 °C) and Category 4 flammable liquids, shall be approved for general use.
Every inside storage room shall be provided with either a gravity or a mechanical exhaust ventilation system. Such system shall be designed to provide for a complete change of air within the room at least six times per hour. If a mechanical exhaust system is used, it shall be controlled by a switch located outside of the door. The ventilating equipment and any lighting fixtures shall be operated by the same switch. A pilot light shall be installed adjacent to the switch if Category 1 or 2 flammable liquids, or Category 3 flammable liquids with a flashpoint below 100 °F (37.8 °C), are dispensed within the room. Where gravity ventilation is provided, the fresh air intake, as well as the exhaust outlet from the room, shall be on the exterior of the building in which the room is located.
1910.106(d)(4)(v) Storage in Inside Storage Rooms
In every inside storage room there shall be maintained one clear aisle at least 3 feet wide. Containers over 30 gallons capacity shall not be stacked one upon the other. Dispensing shall be by approved pump or self-closing faucet only.
1910.106(d)(4)(ii) Rating and Capacity
Storage in inside storage rooms shall comply with Table H-13.
Footnote(1) Fire protection system shall be sprinkler, water
spray, carbon dioxide, or other system.
|Maximum size||Total Allowable
|Yes||2 hours||500 sq. ft.||10|
|No||2 hours||500 sq. ft.||5|
|Yes||1 hour||150 sq. ft.||4|
|No||1 hour.||150 sq. ft.||2|
Related Code Sections
1910.106(d)(4) Hazardous Materials, Design and Construction of Inside Storage Rooms
Inside storage rooms shall be constructed to meet the required fire-resistive rating for their use. Such construction shall comply with the test ...
1910.110(b)(11)(i) Hazardous Materials,
Heating or cooling coils shall not be installed inside a storage container ...
1910.106(g)(1)(iii) Hazardous Materials, Inside Buildings
Special enclosure inside building per 1910.106(f)(1)(ii). 1 Entire enclosure. Sales, storage and rest rooms. (2 ...
1910.106(d)(5) Hazardous Materials, Storage Inside Building
in a storage cabinet or in safety cans or in an inside storage room not having a door that opens into that portion of the building used by the public ...
1910.253(f)(6) Welding, Cutting, and Brazing,
The walls, partitions, floors, and ceilings of inside generator rooms shall be of noncombustible construction having ...