// CODE SNIPPET
508.5.2.1 Department Flow Tests
Related Code Sections
1003.3.4 Traps, Interceptors and Separators, Grease Interceptor and Automatic Grease Removal Device Sizing and Standards
Grease interceptors and automatic grease removal devices shall be sized in accordance with the rules of the Department of Environmental Protection ...
NYC Plumbing Code 2014 > 10 Traps, Interceptors and Separators > 1003 Interceptors and Separators > 1003.3 Grease Interceptors > 1003.3.4 Grease Interceptor and Automatic Grease Removal Device Sizing and Standards
Article 17 Standpipe Systems [PDF] (page 3)
system shall be subjected to a hydrostatic pressure test and to a flow test to demonstrate its suitability for fire department use. The test shall ...
§27-963 Fire Alarm, Detection and Extinguishing Equipment, Direct Connection of Sprinklers to the Public Water System
the requirements of this section. A letter from the bureau of water supply of the department of environmental protection estimating available flow ...
NYC 1968 Code (Vol I) > 17 Fire Alarm, Detection and Extinguishing Equipment > 4 Automatic Sprinkler Requirements > §27-963 Direct Connection of Sprinklers to the Public Water System
903.4.1 Fire Protection Systems, Signals and Monitoring
in roadway boxes provided by the city or a public utility are not required to be monitored. Back flow prevention device test valves, located ...
NYC Building Code 2014 > 9 Fire Protection Systems > 903 Automatic Sprinkler Systems > 903.4 Sprinkler System Supervision and Alarms > 903.4.1 Signals and Monitoring
406.6 Gas Piping Installations, System and Equipment Leakage Test
Leakage testing of systems and equipment shall be in accordance with Sections 406.6.1 through 406.6.4 ...
NYC Fuel Gas Code 2008 > 4 Gas Piping Installations > 406 Inspection, Testing and Purging > 406.6 System and Equipment Leakage Test