// CODE SNIPPET
184.108.40.206.3 DDC Display
Related Code Sections
220.127.116.11.3 Heating, Ventilating, and Air Conditioning, DDC Display
Where DDC is required by Section 18.104.22.168.1 for new buildings , the DDC system shall be capable of trending and graphically displaying input ...
Energy Standard for Buildings Except Low-Rise Residential Buildings 2016 of Illinois > 6 Heating, Ventilating, and Air Conditioning > 6.4 Mandatory Provisions > 6.4.3 Controls and Diagnostics > 22.214.171.124 Direct Digital Control (DDC) Requirements > 126.96.36.199.3 DDC Display
188.8.131.52 Scoping Requirements, Displays
New displays and written information shall be located and designed so that they may be seen by seated persons. New exhibits and signage displayed ...
2018 Illinois Accessibility Code > 2 Scoping Requirements > 202 Existing Buildings and Facilities > 202.5 Alterations to Qualified Historic Buildings and Facilities > 202.5.2 Alterations to Historically Interpreted Buildings > 184.108.40.206 Displays
707.7 Communication Elements and Features, Display Screen
The display screen shall comply with 707.7. EXCEPTION: Drive-up only automatic teller machines and fare machines shall not be required ...
2018 Illinois Accessibility Code > 7 Communication Elements and Features > 707 Automatic Teller Machines and Fare Machines > 707.7 Display Screen
220.127.116.11 Heating, Ventilating, and Air Conditioning, Set-Point Overlap Restriction
; mechanical stops; or, for DDC systems , software programming) shall be provided to prevent the heating set point from exceeding the cooling set ...
Energy Standard for Buildings Except Low-Rise Residential Buildings 2016 of Illinois > 6 Heating, Ventilating, and Air Conditioning > 6.4 Mandatory Provisions > 6.4.3 Controls and Diagnostics > 18.104.22.168 Set-Point Overlap Restriction