Outdoor air supply and exhaust equipment shall be installed with dampers that automatically close upon fan shutdown.
- Where it can be demonstrated to the satisfaction of the enforcing agency that the equipment serves an area that must operate continuously.
- Gravity and other nonelectrical equipment that has readily accessible manual damper controls.
- At combustion air intakes and shaft vents.
- Where prohibited by other provisions of law.