// CODE SNIPPET
E3908.9.1 Cord-And-Plug-Connected Equipment
JUMP TO FULL CODE CHAPTER
By means of an equipment grounding conductor run with the power supply conductors in a cable assembly or flexible cord properly terminated in a grounding-type attachment plug with 1 fixed grounding contact. [250.138(A)]
Exception: The grounding contacting pole of grounding-type plug-in ground-fault circuit interrupters may be of the movable, self-restoring type on circuits operating at not over 150 volts between any 2 conductors or over 150 volts between any conductor and ground. [250.138(A) Exception]
Related Code Sections
E3908.9.1 Power and Lighting Distribution, Cord-And-Plug-Connected Equipment
Noncurrent-carrying metal parts of the cord-and-plug-connected equipment, if grounded, shall be connected to an equipment grounding conductor by 1 ...
2015 Michigan Residential Code > 39 Power and Lighting Distribution > E3908 Grounding > E3908.9 Equipment Fastened in Place or Connected by Permanent Wiring Methods > E3908.9.1 Cord-And-Plug-Connected Equipment
E4001.14 Devices and Luminaries, Cord-And-Plug-Connected Loads
Where snap switches are used to control cord-and-plug-connected equipment on a general-purpose branch circuit, each snap switch controlling ...
2015 Michigan Residential Code > 40 Devices and Luminaries > E4001 Switches > E4001.14 Cord-And-Plug-Connected Loads
E3702.3 Branch Circuit and Feeder Requirements, Fifteen- And 20-Ampere Branch Circuits
of any one cord-and-plug-connected utilization equipment not fastened in place shall not exceed 80 percent of the branch-circuit ampere rating. The ...
2015 Michigan Residential Code > 37 Branch Circuit and Feeder Requirements > E3702 Branch Circuit Ratings > E3702.3 Fifteen- And 20-Ampere Branch Circuits
E4202.2 Swimming Pools, Flexible Cords
other than underwater luminaires, fixed or stationary equipment shall be permitted to be connected with a flexible cord to facilitate removal ...
2015 Michigan Residential Code > 42 Swimming Pools > E4202 Wiring Methods for Pools, Spas, Hot Tubs and Hydromassage Bathtubs > E4202.2 Flexible Cords