// CODE SNIPPET
1107.5.4 Copper Tubing Joints
Related Code Sections
1107.5.4 Refrigeration, Copper Tubing Joints
Copper tubing joints used in refrigerating systems containing Group A2, A3, B2 or B3 refrigerants shall be brazed. Soldered joints shall not be used ...
2015 Michigan Mechanical Code > 11 Refrigeration > 1107 Refrigerant Piping > 1107.5 Materials for Refrigerant Pipe and Tubing > 1107.5.4 Copper Tubing Joints
1209.3.2 Hydronic Piping, Copper Tubing Joints
Copper tubing shall be joined by brazing complying with Section 1203.3.1 ...
2015 Michigan Mechanical Code > 12 Hydronic Piping > 1209 Embedded Piping > 1209.3 Embedded Joints > 1209.3.2 Copper Tubing Joints
705.7.1 Sanitary Drainage, Brazed Joints
All joint surfaces shall be cleaned. An approved flux shall be applied where required. The joint shall be brazed with a filler metal conforming ...
2015 Michigan Plumbing Code > 7 Sanitary Drainage > 705 Joints > 705.7 Copper Tubing > 705.7.1 Brazed Joints
P3003.13.1 Sanitary Drainage, Copper or Copper-Alloy Tubing to Cast-Iron Hub Pipe
Joints between copper or copper-alloy tubing and cast-iron hub pipe shall be made with a copper-alloy ferrule or compression joint. The copper ...
2015 Michigan Residential Code > 30 Sanitary Drainage > P3003 Joints and Connections > P3003.13 Joints Between Different Materials > P3003.13.1 Copper or Copper-Alloy Tubing to Cast-Iron Hub Pipe
1303.7 Fuel Oil Piping and Storage, Copper or Copper-Alloy Tubing
Joints between copper or copper-alloy tubing or fittings shall be brazed, mechanical joints complying with Section 1303.3, press connect joints ...
2015 Michigan Mechanical Code > 13 Fuel Oil Piping and Storage > 1303 Joints and Connections > 1303.7 Copper or Copper-Alloy Tubing