// CODE SNIPPET
P3003.10 Copper Pipe
JUMP TO FULL CODE CHAPTER
All joint surfaces shall be cleaned. An approved flux shall be applied where required. The joint shall be brazed with a filler metal conforming to AWS A5.8.
Mechanical joints shall be installed in accordance with the manufacturer's instructions.
Solder joints shall be made in accordance with the methods of ASTM B 828. All cut tube ends shall be reamed to the full inside diameter of the tube end. All joint surfaces shall be cleaned. A flux conforming to ASTM B 813 shall be applied. The joint shall be soldered with a solder conforming to ASTM B 32.
Threads shall conform to ASME B1.20.1. Pipe-joint compound or tape shall be applied on the male threads only.
Related Code Sections
P3003.10 Sanitary Drainage, Copper Pipe
Joints between copper or copper-alloy pipe or fittings shall comply with Sections P3003.10.1 through P3003.10.4 ...
Residential Code 2012 of South Holland, IL > 30 Sanitary Drainage > P3003 Joints and Connections > P3003.10 Copper Pipe
1203.7 Hydronic Piping, Copper or Copper-Alloy Pipe
Joints between copper or copper-alloy pipe or fittings shall be brazed, mechanical, soldered, threaded or welded joints conforming to Section 1203.3 ...
Mechanical Code 2012 of South Holland, IL > 12 Hydronic Piping > 1203 Joints and Connections > 1203.7 Copper or Copper-Alloy Pipe
1303.6 Fuel Oil Piping and Storage, Copper or Copper-Alloy Pipe
Joints between copper or copper-alloy pipe or fittings shall be brazed, mechanical, threaded or welded joints complying with Section 1303.3 ...
Mechanical Code 2012 of South Holland, IL > 13 Fuel Oil Piping and Storage > 1303 Joints and Connections > 1303.6 Copper or Copper-Alloy Pipe
1107.5.2 Refrigeration, Copper and Brass Pipe
Standard iron-pipe size, copper and red brass (not less than 80-percent copper) pipe shall conform to ASTM B 42 and ASTM B 43 ...
Mechanical Code 2012 of South Holland, IL > 11 Refrigeration > 1107 Refrigerant Piping > 1107.5 Materials for Refrigerant Pipe and Tubing > 1107.5.2 Copper and Brass Pipe