// CODE SNIPPET
A 105.2 Copper and Copper Alloy Piping
Related Code Sections
1220.127.116.11 Fuel Gas Piping, Copper and Copper Alloy Pipe
Copper and copper alloy pipe shall not be used if the gas contains more than an average of 0.3 grains of hydrogen sulfide per 100 standard cubic feet ...
2018 Uniform Plumbing Code of Nevada > 12 Fuel Gas Piping > 1208.0 Gas Piping System Design, Materials, and Components > 1208.6 Acceptable Piping Materials and Joining Methods > 1208.6.3 Metallic Pipe > 118.104.22.168 Copper and Copper Alloy Pipe
1109.1.1 Refrigeration, Copper and Copper Alloy Pipe
Copper and copper alloy refrigeration piping, valves, fittings, and related parts used in the construction and installation of refrigeration systems ...
2018 Uniform Mechanical Code of Nevada > 11 Refrigeration > 1109.0 Refrigeration Piping, Containers, and Valves > 1109.1 Materials > 1109.1.1 Copper and Copper Alloy Pipe
A 105.2 Recommended Rules for Sizing the Water Supply System, Copper and Copper Alloy Piping
Where copper tubing or copper alloy pipe is to be used for the supply piping and where the character of the water is such that slight changes ...
2018 Uniform Plumbing Code of Nevada > A Recommended Rules for Sizing the Water Supply System > A 105.0 Size of Building Supply > A 105.2 Copper and Copper Alloy Piping
1211.4 Hydronics, Copper or Copper Alloy Pipe and Tubing
or copper alloy pipe, tubing, or fittings shall be made with brazing alloys having a liquid temperature above 1000°F (538°C). The joint surfaces ...
2018 Uniform Mechanical Code of Nevada > 12 Hydronics > 1211.0 Joints and Connections > 1211.4 Copper or Copper Alloy Pipe and Tubing
P3003.6 Sanitary Drainage, Copper and Copper-Alloy Pipe and Tubing
Joints between copper or copper-alloy pipe tubing or fittings shall comply with Sections P3003.6.1 through P3003.6.4 ...
Residential Code 2018 of Nevada > 30 Sanitary Drainage > P3003 Joints and Connections > P3003.6 Copper and Copper-Alloy Pipe and Tubing