// CODE SNIPPET
P3003.6 Copper and Copper-Alloy Pipe and Tubing
JUMP TO FULL CODE CHAPTER
All joint surfaces shall be cleaned. An approved flux shall be applied where required. Brazing materials shall have a melting point in excess of 1,000°F (538°C). Brazing alloys filler metal shall be in accordance with AWS A5.8.
Mechanical joints shall be installed in accordance with the manufacturer's instructions.
Copper and copper-alloy joints shall be soldered in accordance with ASTM B828. Cut tube ends shall be reamed to the full inside diameter of the tube end. All joint surfaces shall be cleaned. Fluxes for soldering shall be in accordance with ASTM B813 and shall become noncorrosive and nontoxic after soldering. The joint shall be soldered with a solder conforming to ASTM B32.
Threads shall conform to ASME B1.20.1. Pipe-joint compound or tape shall be applied on the male threads only.
Related Code Sections
P3003.6 Sanitary Drainage, Copper and Copper-Alloy Pipe and Tubing
Joints between copper or copper-alloy pipe tubing or fittings shall comply with Sections P3003.6.1 through P3003.6.4 ...
2017 FBC - Residential, 6th edition > 30 Sanitary Drainage > P3003 Joints and Connections > P3003.6 Copper and Copper-Alloy Pipe and Tubing
M2202.1 Special Piping and Storage Systems, Materials
Piping shall consist of steel pipe, copper and copper alloy pipe and tubing or steel tubing conforming to ASTM A539. Aluminum tubing shall ...
2017 FBC - Residential, 6th edition > 22 Special Piping and Storage Systems > M2202 Oil Piping, Fitting and Connections > M2202.1 Materials
M2103.1 Hydronic Piping, Piping Materials
Piping for embedment in concrete or gypsum materials shall be standard-weight steel pipe, copper and copper alloy pipe and tubing, cross-linked ...
2017 FBC - Residential, 6th edition > 21 Hydronic Piping > M2103 Floor Heating Systems > M2103.1 Piping Materials
M2101.9 Hydronic Piping, Piping Support
3 5 CPVC ≥1 1 / 4 inches 4 10 Copper or copper alloy pipe 12 10 Copper or copper alloy tubing 6 10 PB pipe or tubing 2.67 4 ...
2014 FBC - Residential, 5th edition > 21 Hydronic Piping > M2101 Hydronic Piping Systems Installation > M2101.9 Piping Support
P2906.17.1 Water Supply and Distribution, Copper or Copper-Alloy Tubing to Galvanized Steel Pipe
Joints between copper or copper-alloy tubing and galvanized steel pipe shall be made with a copper alloy fitting or dielectric fitting. The copper ...
2017 FBC - Residential, 6th edition > 29 Water Supply and Distribution > P2906 Materials, Joints and Connections > P2906.17 Joints Between Different Materials > P2906.17.1 Copper or Copper-Alloy Tubing to Galvanized Steel Pipe