// CODE SNIPPET
403.4.3 Copper and Brass
JUMP TO FULL CODE CHAPTER
Related Code Sections
403.4.3 Gas Piping Installations, Copper and Brass
Copper and brass pipe shall not be used if the gas contains more than an average of 0.3 grains of hydrogen sulfide per 100 standard cubic feet of gas ...
Fuel Gas Code 2012 of Tennessee > 4 Gas Piping Installations > 403 (IFGS) Piping Materials > 403.4 Metallic Pipe > 403.4.3 Copper and Brass
1107.5.2 Refrigeration, Copper and Brass Pipe
Standard iron-pipe size, copper and red brass (not less than 80-percent copper) pipe shall conform to ASTM B 42 and ASTM B 43 ...
Mechanical Code 2012 of Tennessee > 11 Refrigeration > 1107 Refrigerant Piping > 1107.5 Materials for Refrigerant Pipe and Tubing > 1107.5.2 Copper and Brass Pipe
G2414.5.2 Fuel Gas, (403.5.2) Copper Tubing
Copper tubing shall comply with standard Type K or L of ASTM B 88 or ASTM B 280. Copper and brass tubing shall not be used if the gas ...
Residential Code 2009 of Tennessee > 24 Fuel Gas > G2414 (403) Piping Materials > G2414.5 (403.5) Metallic Tubing > G2414.5.2 (403.5.2) Copper Tubing
(B) Special Equipment, Underwater Junction Boxes and Other Underwater Enclosures
or compression glands or seals for cord entry. (b) Underwater enclosures shall be submersible and made of copper, brass, or other approved corrosion ...
National Electrical Code 2017 of Tennessee > 6 Special Equipment > 680 Swimming Pools, Fountains, and Similar Installations > 680.52 Junction Boxes and Other Enclosures > (B) Underwater Junction Boxes and Other Underwater Enclosures
(2) Special Equipment, Installation
as required. Where the junction box is supported only by conduits in accordance with 314.23(E) and (F), the conduits shall be of copper, brass, stainless ...
National Electrical Code 2017 of Tennessee > 6 Special Equipment > 680 Swimming Pools, Fountains, and Similar Installations > 680.52 Junction Boxes and Other Enclosures > (B) Underwater Junction Boxes and Other Underwater Enclosures > (2) Installation