// CODE SNIPPET
1010.1.9.6 Controlled Egress Doors in Groups I-1 and I-2
JUMP TO FULL CODE CHAPTER
This section has been amended at the state or city level.
Electric locking systems, including electromechanical locking systems and electromagnetic locking systems, shall be permitted to be locked in the means of egress in Group I-1 or I-2 occupancies where the clinical needs of persons receiving care require their containment. Controlled egress doors shall be permitted in such occupancies where the building is equipped throughout with an automatic sprinkler system in accordance with Section 903.3.1.1 or an approved automatic smoke or heat detection system installed in accordance with Section 907, provided that the doors are installed and operate in accordance with all of the following:
- The door locks shall unlock on actuation of the automatic sprinkler system or automatic fire detection system.
- The door locks shall unlock on loss of power controlling the lock or lock mechanism.
- The door locking system shall be installed to have the capability of being unlocked by a switch located at the fire command center, a nursing station or other approved location. The switch shall directly break power to the lock.
- A building occupant shall not be required to pass through more than one door equipped with a controlled egress locking system before entering an exit.
- The procedures for unlocking the doors shall be described and approved as part of the emergency planning and preparedness required by Chapter 4 of the International Fire Code.
- All clinical staff shall have the keys, codes or other means necessary to operate the locking systems.
- Emergency lighting shall be provided at the door.
- The door locking system units shall be listed in accordance with UL 294.
The secure area or unit with special egress locks shall be located at the level of exit discharge in Type V construction.
- Items 1 through 4 shall not apply to doors to areas occupied by persons who, because of clinical needs, require restraint or containment as part of the function of a psychiatric treatment area.
- Items 1 through 4 shall not apply to doors to areas where a listed egress control system is utilized to reduce the risk of child abduction from nursery and obstetric areas of a Group I-2 hospital.
Related Code Sections
1010.1.9 Means of Egress, Door Operations
in Group I-1 or I-2 occupancies where the clinical needs of persons receiving care require their containment. Controlled egress doors shall be permitted ...
Building Code 2015 of Utah > 10 Means of Egress > 1010 Doors, Gates and Turnstiles > 1010.1 Doors > 1010.1.9 Door Operations
Section 408 Special Detailed Requirements Based on Use and Occupancy, Group I-3
In occupancies in Group I-3, windows and doors in 1-hour fire ...
Building Code 2015 of Utah > 4 Special Detailed Requirements Based on Use and Occupancy > 408 Group I-3
Section 408 Special Detailed Requirements Based on Occupancy and Use, Group I-3
in Group I-3 occupancies where security operations necessitate the locking of required means of egress shall be permitted to be classified as a different ...
Building Code 2018 of Utah > 4 Special Detailed Requirements Based on Occupancy and Use > 408 Group I-3