// CODE SNIPPET
E 503.5.1.1 Control Signal
JUMP TO FULL CODE CHAPTER
Economizer controls shall be capable of and configured to sequence the dampers with the mechanical cooling equipment and shall not be controlled by only mixed air temperature.
Exception: The use of mixed air temperature limit control shall be permitted for systems controlled from space temperature (such as single-zone systems). [ASHRAE 90.1:22.214.171.124.2]