// CODE SNIPPET
184.108.40.206.2 Control Signal
Go To Full Code Chapter
Economizer controls shall be capable of and configured to sequence the dampers with the mechanical cooling equipment and shall not be controlled by only mixed-air temperature.
Exception to 220.127.116.11.2
The use of mixed-air temperature limit control shall be permitted for systems controlled from space temperature (such as single-zone systems).
Related Code Sections
18.104.22.168.2 Heating, Ventilating, and Air Conditioning, Control Signal
Economizer controls shall be capable of and configured to sequence the dampers with the mechanical cooling equipment and shall not be controlled ...
(I) Wiring and Protection, Remote-Control, Signaling, and Fire Alarm Circuits
, by Class 2 and Class 3 remote-control and signaling circuits, and by fire alarm circuits shall be grounded where system grounding is required ...
(4) Wiring and Protection, Control and Signal Circuits
Each control or signal circuit shall be observed to perform its proper control function or produce a correct signal output ...
(B) Special Equipment, Control and Signal Purposes
Collector rings for control and signal purposes shall have a current rating not less than 125 percent of the full-load current of the largest device ...
Chapter 43 Class 2 Remote-Control, Signaling and Power-Limited Circuits
ICC user note: About this chapter: Chapter 43 covers low-voltage power-limited circuits such as alarm, door bell, remote control and signaling ...