// CODE SNIPPET
402.2.3 Control and Accessibility
Related Code Sections
402.2.3 Ventilation Air, Control and Accessibility
The means to open required operable openings shall be readily accessible to building occupants where the space is occupied. Controls shall ...
2018 Uniform Mechanical Code of Nevada > 4 Ventilation Air > 402.0 Ventilation Air > 402.2 Natural Ventilation > 402.2.3 Control and Accessibility
22.214.171.124.7* Installation Requirements, Control Valve Accessibility
All control valves shall be located where accessible and free of obstructions ...
Standard for the Installation of Sprinkler Systems 2016 of Nevada > 8 Installation Requirements > 8.16 Piping Installation > 8.16.1 Valves > 126.96.36.199* Control Valves > 188.8.131.52.7* Control Valve Accessibility
E 602.1.1.3 Sustainable Practices, Accessible Damper Control
The flue damper shall have a readily accessible control. Exception: Where a gas log, log lighter, or decorative gas appliance is installed ...
2018 Uniform Mechanical Code of Nevada > E Sustainable Practices > E 602.0 Fireplaces > E 602.1 Requirements > E 602.1.1 Masonry or Factory-Built Fireplace > E 602.1.1.3 Accessible Damper Control
1008.1.9.8 Means of Egress, Access-Controlled Egress Doors
in occupancies in Groups A, B, E, I-2, M, R-1 or R-2, are permitted to be equipped with an approved entrance and egress access control system, listed ...
Building Code 2012 of Nevada > 10 Means of Egress > 1008 Doors, Gates and Turnstiles > 1008.1 Doors > 1008.1.9 Door Operations > 1008.1.9.8 Access-Controlled Egress Doors
(B) Communications Systems, Grounding of Controls
All external metal handles and controls accessible to the operating personnel shall be effectively connected to an equipment grounding conductor ...
National Electrical Code 2017 of Nevada > 8 Communications Systems > 810 Radio and Television Equipment > 810.71 General > (B) Grounding of Controls