// CODE SNIPPET
[F] 909.13 Control Air Tubing
JUMP TO FULL CODE CHAPTER
Control air tubing shall be of sufficient size to meet the required response times. Tubing shall be flushed clean and dry prior to final connections and shall be adequately supported and protected from damage. Tubing passing through concrete or masonry shall be sleeved and protected from abrasion and electrolytic action.
Control-air tubing shall be hard-drawn copper, Type L, ACR in accordance with ASTM B42, ASTM B43, ASTM B68, ASTM B88, ASTM B251 and ASTM B280. Fittings shall be wrought copper or brass, solder type in accordance with ASME B16.18 or ASME B16.22. Changes in direction shall be made with appropriate tool bends. Brass compression-type fittings shall be used at final connection to devices; other joints shall be brazed using a BCuP-5 brazing alloy with solidus above 1,100°F (593°C) and liquids below 1,500°F (816°C). Brazing flux shall be used on copper-to-brass joints only.
Exception: Nonmetallic tubing used within control panels and at the final connection to devices provided that all of the following conditions are met:
- Tubing shall comply with the requirements of Section 602.2.1.3 of the International Mechanical Code.
- Tubing and connected devices shall be completely enclosed within a galvanized or paint-grade steel enclosure having a minimum thickness of 0.0296 inch (0.7534 mm) (No. 22 gage). Entry to the enclosure shall be by copper tubing with a protective grommet of neoprene or Teflon or by suitable brass compression to male barbed adapter.
- Tubing shall be identified by appropriately documented coding.
- Tubing shall be neatly tied and supported within the enclosure. Tubing bridging cabinets and doors or moveable devices shall be of sufficient length to avoid tension and excessive stress. Tubing shall be protected against abrasion. Tubing connected to devices on doors shall be fastened along hinges.
Control tubing serving other than smoke control functions shall be isolated by automatic isolation valves or shall be an independent system.
Control air tubing shall be tested at three times the operating pressure for not less than 30 minutes without any noticeable loss in gauge pressure prior to final connection to devices.
Related Code Sections
909.13 Fire Protection and Life Safety Systems, Control Air Tubing
Control air tubing shall be of sufficient size to meet the required response times. Tubing shall be flushed clean and dry prior to final connections ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 909 Smoke Control Systems > 909.13 Control Air Tubing
415.11.6 Special Detailed Requirements Based on Occupancy and Use, Piping and Tubing
Hazardous production materials piping and tubing shall comply with this section and ASME B31.3 ...
Building Code 2018 of Illinois > 4 Special Detailed Requirements Based on Occupancy and Use > 415 Groups H-1, H-2, H-3, H-4 and H-5 > 415.11 Group H-5 > 415.11.6 Piping and Tubing
7220.127.116.11 Fire and Smoke Protection Features, Smoke Damper Actuation
the duct with sampling tubes protruding into the duct. The detector or tubes within the duct shall be within 5 feet (1524 mm) of the damper . Air ...
Building Code 2018 of Illinois > 7 Fire and Smoke Protection Features > 717 Ducts and Air Transfer Openings > 717.3 Damper Testing, Ratings and Actuation > 717.3.3 Damper Actuation > 718.104.22.168 Smoke Damper Actuation
725.31 Special Conditions, Safety-Control Equipment
household heating and air conditioning shall not be considered safety-control equipment ...
National Electrical Code 2017 of Illinois > 7 Special Conditions > 725 Class 1, Class 2, and Class 3 Remote-Control, Signaling, and Power-Limited Circuits > 725.31 Safety-Control Equipment
517.78 Special Occupancies, Guarding and Grounding
All high-voltage parts, including X-ray tubes, shall be mounted within grounded enclosures. Air, oil, gas, or other suitable insulating media shall ...
National Electrical Code 2017 of Illinois > 5 Special Occupancies > 517 Health Care Facilities > 517.78 Guarding and Grounding