// CODE SNIPPET
A 103.2 Continuous Supply Demand
Related Code Sections
A 103.2 Recommended Rules for Sizing the Water Supply System, Continuous Supply Demand
Estimate continuous supply demands in gallons per minute (gpm) (L/s) for lawn sprinklers, air conditioners, etc., and add the sum to the total demand ...
2018 Uniform Plumbing Code of Nevada > A Recommended Rules for Sizing the Water Supply System > A 103.0 Demand Load > A 103.2 Continuous Supply Demand
M 102.5 Peak Water Demand Calculator, Continuous Supply Demand
Continuous supply demands in gallons per minute (gpm) for lawn sprinklers, air conditioners, hose bibbs, etc., shall be added to the total estimated ...
2018 Uniform Plumbing Code of Nevada > M Peak Water Demand Calculator > M 102.0 Demand Load > M 102.5 Continuous Supply Demand
E 805.3.1.2 Sustainable Practices, Functional Testing
applicable). Step 2: Simulate a heating demand during the occupied condition. Verify and document the following: Supply fan operates continually ...
2018 Uniform Mechanical Code of Nevada > E Sustainable Practices > E 805.0 HVAC System Tests > E 805.3 Constant Volume, Single-Zone, Unitary Air Conditioner and Heat Pumps Systems Acceptance (Form MECH-3A) > E 805.3.1 Test Procedure > E 805.3.1.2 Functional Testing