// CODE SNIPPET
706.4 Continuity of Fire Barrier Walls
Go To Full Code Chapter
Fire barrier walls shall extend from the top of the floor/ceiling assembly below to the underside of the floor or roof slab or deck above and shall be securely attached thereto. These walls shall be continuous through concealed spaces such as the space above a suspended ceiling. The supporting construction for fire barrier walls shall be protected to afford the required fire-resistance rating of the fire barrier supported except for 1-hour fire-resistance-rated incidental use area separations as required by Table 508.2 in buildings of Type IIB, IIIB and VB construction. Hollow vertical spaces within the fire barrier wall shall be fire-stopped at every floor level.
1. The maximum required fire-resistance rating for assemblies supporting fire barriers separating tank storage as provided for in Section 4126.96.36.199 shall be 2 hours, but not less than required by Table 601 for the building construction type.
Related Code Sections
706.4 Fire-Resistance-Rated Construction, Continuity of Fire Barrier Walls
Fire barrier walls shall extend from the top of the floor/ceiling assembly below to the underside of the floor or roof slab or deck above and shall ...
7.2.1 Fire Barrier Walls,
Fire barrier walls shall be continuous from one of the following or a combination thereof: An exterior wall to an exterior wall A floor below ...
1021.2 Means of Egress, Separation
buildings is more than 20 feet (6096 mm). Horizontal exit walls constructed as fire barriers shall be continuous from exterior wall to exterior wall so ...
709.4 Fire and Smoke Protection Features, Continuity
Smoke-barrier walls used to separate smoke compartments shall form an effective membrane continuous from outside wall to outside wall ...
709.4 Fire-Resistance-Rated Construction, Continuity
Smoke barriers shall form an effective membrane continuous from outside wall to outside wall and from floor slab to floor or roof deck above ...