// CODE SNIPPET
E3908.13 Continuity and Attachment of Equipment Grounding Conductors to Boxes
JUMP TO FULL CODE CHAPTER
Where circuit conductors are spliced within a box or terminated on equipment within or supported by a box, any equipment grounding conductors associated with the circuit conductors shall be connected within the box or to the box with devices suitable for the use. Connections depending solely on solder shall not be used. Splices shall be made in accordance with Section E3406.10 except that insulation shall not be required. The arrangement of grounding connections shall be such that the disconnection or removal of a receptacle, luminaire or other device fed from the box will not interfere with or interrupt the grounding continuity. [250.146(A) and (C)]
Related Code Sections
E3908.13 Power and Lighting Distribution, Continuity and Attachment of Equipment Grounding Conductors to Boxes
Where circuit conductors are spliced within a box or terminated on equipment within or supported by a box, any equipment grounding conductors ...
2015 Michigan Residential Code > 39 Power and Lighting Distribution > E3908 Grounding > E3908.13 Continuity and Attachment of Equipment Grounding Conductors to Boxes
E3610.3 Services, Raceways and Enclosures for Grounding Electrode Conductors
Ferrous metal raceways and enclosures for grounding electrode conductors shall be electrically continuous from the point of attachment to cabinets ...
2015 Michigan Residential Code > 36 Services > E3610 Grounding Electrode Conductors > E3610.3 Raceways and Enclosures for Grounding Electrode Conductors
Section E4205 Swimming Pools, Grounding
but not smaller than 12 AWG. The equipment grounding conductor between the wiring chamber of the secondary winding of a transformer and a junction box shall ...
E4001.11.1 Devices and Luminaires, Faceplate Grounding
or metal cover that is connected to an equipment grounding conductor or to a nonmetallic box with integral means for connecting to an equipment grounding ...
2015 Michigan Residential Code > 40 Devices and Luminaires > E4001 Switches > E4001.11 Snap Switch Faceplates > E4001.11.1 Faceplate Grounding
Section E3407 General Requirements, Conductor and Terminal Identification
Insulated grounded conductors of sizes 6 AWG or smaller shall be identified by a continuous white or gray outer finish or by three continuous white ...
2015 Michigan Residential Code > 34 General Requirements > E3407 Conductor and Terminal Identification